Quadrulex Service Drop Wire meets or exceeds the following ASTM specifications:
B-230 Aluminum Wire, 1350-H19 for Electrical Purposes.
B-231 Aluminum Conductors, Concentric-Lay-Stranded.
B-232 Aluminum Conductors, Concentric-Lay-Stranded, Coated Steel Reinforced (ACSR).
B-399 Concentric-Lay-Stranded 6201-T81 Aluminum Alloy Conductors.
B498 Zinc-Coated Steel Core Wire for Aluminum Conductors, Steel Reinforced (ACSR).
Service Drop cable meets or exceeds all applicable requirements of ANSI/ICEA S-76-474.
Quadruplex service drop wire is used to supply 3 phase power, usually from a pole mounted transformer to the user’s service head where connection to the service entrance cable is made. To be used at voltages of 600 volts or less phase to phase and at conductor temperatures not to exceed 75°C for polyethylene insulated conductors or 90°C for crosslinked polyethylene (XLP) insulated conductors.
Quadrulex Service Drop Wire consists of Concentric strand or compressed 1350-H19 conductor, polyethylene or crosslinked polyethylene insulation, concentric strand AAC, ACSR, or 6201 alloy neutral messenger.